Quadruplex Aluminum Cable Type Mobile Home Feeder
Select gauge from drop-down menu for prices:
Applications: Mobile Home Feeder Cable is mainly used for supplying the energy required within the mobile home. The cable is designed for use at 600 volts or less and conductor temperatures not exceeding 90C.
Installation: Suitable for direct burial or underground installations and in raceways.
Construction: Quadruplexed tye USE-2 or RHH or RHW-2 compact stranded AA-8000 Series aluminum alloy conductors. Insulation is sunlight-resistant Cross-linked Polyethylene (XLPE). Neutral is identified by triple extruded white stripes and Grounding is identified by total green surface coating.
Aluminum URD Cable & Wire
The aluminum URD wire is rated at 600v, used for underground distribution and service entry applications not exceeding 90 degrees Celsius. It can be directly submerged in earth or fitted in context with wet or dry conditions. It’s a Class B compacted of concentric lay stranded 1350 aluminum compound of ASTM B231 or AA-8000 aluminum blend with ASTM B800&B801. Its phase conductors in black thermoset cross-linked polyethylene (XLPE). Neutral Rod in black thermoset cross-linked polyethylene (XLPE) identified by yellow striping or full yellow jacket.
The single conductor aluminum cable type UD, is a minor installation for an underground service. Where it’s likely used for installation to a barn, house or some type of secondary fitting that requires subversive service of 600 volts or lower. Four solitary aluminum wires can be used in applications for hinges or to power an energy basis. The cable can be used lacking any protection and just buried in the ground. It has the construction of rods which are stuck, and compressed 1350-H19, H16 or H26 aluminum, insulated with vulcanized interwoven polyethylene (VIP 1).
Aluminum Type URD Duplex Cable Wire, Straight Burial 600 Volts Applications which can be directly buried or installed, 600 volt secondary distribution. Construction Concentric stranded or compressed 1350-H19 aluminum conductor, cross linked polyethylene protection. Protected rods surface printed, always a neutral triple yellow striped. Black neutrals may be specified if one desires so. Standards Secondary UD duplex conductor 600V cable meets or surpasses the following ASTM terms: B-230 Aluminum Wire, 1350-H19 for Electrical Purposes. B-231 Aluminum 1350 conductors, Concentric-Lay-Stranded. B-786 19 Wire combination unilay-stranded Aluminum Conductors for subsequent insulation.
Secondary UD triplex conductor 600V cable meets or exceeds the following ASTM specifications: B-230 Aluminum Wire, 1350-H19 for Electrical Purposes, B-231 Aluminum 1350 conductors, Concentric-Lay-Stranded. B-786 "19 Wire combination unilay-stranded Aluminum Conductors for subsequent insulation”, B-901 "Compressed round stranded Aluminum Conductors using single input wire construction". Also the Secondary UD triplex conductor 600V cable can meet all appropriate requirements of ICEA S-105-692, or even exceed the valid requirements.
The Quadruplex Aluminium Cable Type URD is concentric stranded or dense 1350-H19 aluminum conductors,also cross-linked polyethylene insulation. Protected rods surface printed, neutral triple yellow striped. Three phase and one neutral rod cabled composed (LH lay) or parallel if so stated. Black neutrals may be specified is wanted.
Quadruplex Aluminum Mobile Home Feeder is also graded at 600 volts, the wire is sunlight resistant and is accepted for use in agreement with the approvals of the National Electrical Code in channels and underground installations. Aluminum blend conductor is recognized by ASTM in Standards B800 and B801.
Model #Triplex Aluminum Cable Type URD
Model #Quadruplex Aluminum Cable Type URD
Model #Aluminum Type MC-XHHW Al Conductors
Model #Aluminum Alumaflex Type MC Jacketed
Model #XHHW-2 Aluminum Conductor
Model #Welding Cable
Model #DLO Diesel Locomotive Cable 2kV
Model #SOOW Portable Cord 600V
Model #SJOOW Portable Cord 300V